How Federated uses fans to further sustainability
A Canadian retail co-op has embraced sustainability to reduce its costs and return the savings to its members and customers.
Warehouse in the NewsCEMA reports December booked orders up 10.2% over December 2015 QPSI announces acquisition of pharmaceutical packaging company, International Labs SencorpWhite names Chris Lingamfelter president of White Systems Swisslog WDS Americas opens new Americas Technology Center in California NRF calls for 3.7 to 4.2 percent annual increase for 2017 retail sales More Warehouse News
Warehouse ResourceParts and Parcels: Handling the Holiday Rush Automation, software help omni-channel retailers and e-tailers manage the demands of small parcel shipping
With the cost of heating the Saskatoon warehouse going through the roof—literally—Federated Co-operatives was interested in testing whether thermal destratification in its warehouses would result in significant heat cost reductions and the reduction of the amount of natural gas needed to heat its facilities. Destratification is what happens when layers of warm air that form in one part of a facility mix with layers of cooler air in another part of a facility to produce a constant temperature.
According to Trevor Carlson, environmental and technical services manager, Federated believed a fair amount of heat was being trapped or lost through the ceiling. The difference between the temperature of the air at the floor level and the underside of the roof deck in some distribution centers can be up to 30 degrees, depending on the time of year. If that warm air could be brought down to circulate through the building, then Federated could reduce the rate at which its buildings were shedding heat through the roof.
To put the theory to the test, Federated installed five 24-foot large-diameter, low-speed fans (Big Ass Fans) in the 80,000-square-foot loading dock area back in 2007. The retail co-operative then began to measure its heat index in the pilot area, a measurement that relates the day’s temperature to the energy demands of the heating system. The index is expressed as Btu/ft2/degree day. Before the installation of the fans, the heat index was 4.49 Btu/ft2/degree day. By the end of 2008, the heat index had been reduced by 10% to 3.61 Btu/ft2/F.
Since then, Federated has expanded the use of fans to other facilities, says Philip Thiemann, warehouse operations director. In Winnipeg, for instance, the co-op installed a fan in a temperature controlled dock area where hot air was building up in the hot summer months around the dock doors.
“We had to turn the thermostats down, which put a constant demand on the refrigeration units,” he says. “The air movement from the fans allows the air to mix and even out the temperatures.” In the process, Thiemann adds, workers have found that the new fans keep the ambient temperature areas more comfortable on hot days for less money.
“The big fans use about 3 amps an hour compared to 180 amps for the fans we had been using in the summer,” he says. “The electrical savings in the summer are greater than the gas savings in the winter and the workers are more comfortable.”
About the AuthorBob Trebilcock Bob Trebilcock, editorial director, has covered materials handling, technology, logistics and supply chain topics for nearly 30 years. In addition to Supply Chain Management Review, he is also Executive Editor of Modern Materials Handling. A graduate of Bowling Green State University, Trebilcock lives in Keene, NH. He can be reached at 603-357-0484.
Subscribe to Modern Materials Handling Magazine!Subscribe today. It's FREE!
Find out what the world’s most innovative companies are doing to improve productivity in their plants and distribution centers.
Start your FREE subscription today!
Automated Storage on the Move Receiving 101: Setting the Table for Success View More From this Issue